ibis Hotel – service request
ClientStarboard Hotels Group
Locationibis Styles Hotel - Barnsley
SectorHotels & Leisure
RequirementsAttend a service request
ObjectiveResolve performance issues
Fixing something when it goes wrong is one approach, though when we were asked to attend the ibis Styles Hotel in Barnsley, it was clear that more was required for a satisfactory solution to their problem.
It was clear to see that the condition of the pipe insulation would be a contributory factor to the performance issues the hotel was encountering, as there would be significant efficiency loses.
Looking inside the inspection hatches on the air handling unit we found blocked filters, and the one remaining drive belt near to failure with the other snapped and lying in the base of the unit.
Drive belts, filters, and insulation renewed, mechanical protection was added to the exposed pipe runs to mitigate the risk of damage recurring.